Water Treatment for Boiler Feed
Generally, boilers are used in industry to generate steams or hot water which in terms to generate power and heat for various applications. These days, modern boilers require High-Quality Water to operate efficiently, but such water can never be obtained from any of the natural water sources. The presence of impurities in the water makes it unfit to use in the boilers. Therefore, water purification systems must be needed for boiler feed makeup water.
ROTEK has been supplying water treatment systems for boiler feed for the past 2 decades. There are generally 3 methods to treat boiler feed water depending on the type of boiler that the customer is using.
ROTEK uses a variety of water purification technologies including:
Pretreatment -> Water Softening (for Hot Water boiler)
Pretreatment -> Reverse Osmosis System (for Industrial Steam boiler)
Pretreatment -> RO System -> EDI or DI Systems (for Power Plant)
Feed-water purity is a matter both of quantity of impurities and nature of impurities: some impurities such as hardness, iron and silica are of more concern, for example, than sodium salts. The purity requirements for any feed-water depend on how much feed water is used as well as what the particular boiler design (pressure, heat transfer rate, etc.) can tolerate. Feed-water purity requirements therefore can vary widely. A low-pressure fire-tube boiler can usually tolerate high feed-water hardness with proper treatment while virtually all impurities must be removed from water used in some modern, high-pressure boilers.
Based on the raw water quality analysis, we will provide our design suggestions follow by the 4 major treatment setup:
This section is basically responsible to filter out most of the fine particles, heavy metals, chlorine, organic matters, bacteria, color & odors. The filtration system usually consists of Clino-X Multimedia Sand Filter, Activated Carbon Filter, Water Softener, Ultra-Filtration System, Anti-Scale, and Chlorination Chemical Dosing Systems.
Reverse osmosis (RO) is a water purification technology that ROTEK uses most of the time for many industries. RO can remove many types of molecules and ions from solutions and is used in both industrial processes and to produce potable water. Depending on the raw water quality, if raw water TDS is below 50ppm, then this section of the purification system may not be required as part of the design for bottled water production.
Although RO removes everything from the water (including good and bad minerals),
however low mineralized water have few adverse effects:
- High corrosion potential
- Dietary deficiency causing risks of ischaemic heart and cerebrovascular disease (WHO, 2005a; WHO, 2006; Cotruvo, 2006)
The WHO recommends 10 mg/L of Magnesium and 30 mg/L of Calcium for drinking water. Therefore adding beneficial minerals to the product water is a process called demineralization. ROTEK uses natural minerals called "Camag" for adding pure Magnesium and Calcium to the product water with great improvement on the taste and pH level.
The most common bacteria found in bottled water is Pseudomonas fluorescens, which is common in fresh-water springs. It is not considered to be a health threat until you leave the bottle open for extended periods of time and the bacteria begin to react with the carcinogens in the plastic. Reducing bacteria and microbial to the minimum is the most important issue in the bottled water production business. ROTEK disinfection system consists of UV sterilizer, Nanosilver Activated Carbon, 0.2-micron filter, and ozone disinfection. With four levels of protections, the ROTEK disinfection system will make sure the bacteria level is reduced to nil before filled to the bottle.